Provided by: nut_2.0.3-4build1_i386
sms - Driver for Brazilian SMS UPS equipment
This man page only documents the hardware‐specific features of the sms
driver. For information about the core driver, see nutupsdrv(8).
This driver has been tested with :
Manager III 650 VA
Manager III 1300 VA
Manager III 650 VA sinusoidal
Manager III 1300 VA sinusoidal
Sinus Single 2000 VA sinusoidal on‐line
Please report another SMS working models, or send‐me the driver
This driver does not support any extra settings in the ups.conf(5).
test.battery.stop ‐ Cancel battery test
test.battery.start ‐ Run battery test until battery is low
test.failure.start ‐ Simulate power failure
shutdown.return ‐ Shut down in .3 minutes and restart in .3 minutes
shutdown.stayoff ‐ Shut down in .3 minutes and do not return
shutdown.stop ‐ Stop a shutdown command
reset.watchdog ‐ Shutdown in 5 minutes and restart in 3 minutes. Call
this with upscmd in crontab every minute.
Marcio Gomes <firstname.lastname@example.org>
The core driver:
The NUT (Network UPS Tools) home page: http://www.networkupstools.org/
Mon Jul 14 2003 SMS(8)